for Wilton, CA
Very good overall service
JIM - Wilton, CA
Quick to respond
JENNIFER - Wilton, CA
Quick to respond to request for system check!
Had to wait three weeks for a part during the coldest part of the year
KEN Jackson - Wilton, CA
Had to wait three weeks for a part for our heating system during the coldest part of the year.
Response from Huft Heating and air Conditioning, Inc.:
I completely agree with your frustration in regards to waiting 3 weeks for the repair part, I would feel the same way. However, we had no control over the manufacturer or the shipping company. I assume the actual service provided by Chuc was not a 1 star rating, just the fact you had to wait for the part to arrive being the reason for it. I apologize for the inconvenience and frustration you had to deal with.
SHIRLEY - Wilton, CA
Toni - Wilton, CA
Absolute great service and polite
ROBERT - Wilton, CA
They told me everything kept me informed. Very polite. Jet and Larry were exceptional.
Performed tuneup on a Goodman furnace. Found capacitor below manufacture specifications. Recommend replacing. All other checks are within manufacturer specifications. System is operational at this time.
Check system operation: customer has concern with water leakage and Living room not heating. Upon arrival, system was working properly with both zone. Check drain lines at all connections and all are tight and secured. No issues and assure customer that System and are operating good and properly at this time.
Preformed furnace tuneup on a Goodman heat pump system I added a iwave to the system no issues or concerns at this time system is operational
Preformed furnace tuneup on a Amana system client changes filter regularly no issues or concerns at this time system is operational
Performed heating inspection on Trane heat pump package unit. All checks are within manufacturer specifications. System is operational at this time.
Performed diagnostic on York furnace. Thermostat seemed to not be fully connected. Pushed thermostat all the way in. Tested system a few times and let it run for about 5-10 min. System seem to be operational at this time.
Performed diagnostic. Found stuck txv. Must order and return.
Replaced the heat strips relay on a Carrier heat pump system. Tested operations. System operations ok at this time.
Replaced a txv on a Amana heat pump unit and charged unit to proper levels. System operations ok at this time.
Replace blower motor on a trane xl1400 heat pump system. Tested system and system is operational at this time.