for Roseville, CA
5 Star Service
LIZ - Roseville, CA
The people are top notch, the service is top notch and so is the quality and price. I can't say enough good things and this company and it's people.
NIC - Roseville, CA
Andre filled in for our normal tech who was out sick. He was very thorough explaining how our system was operating and what issues to keep tabs on. Overall, he provided great customer service, which is what we have come to expect from Huft.
LIZ - Roseville, CA
Huft did the original install when my hvac unit had to be replaced. It was no easy task as mine is on the roof of a house built in 1918. They were on time on budget.. this was back in 2015. They have been doing my check ups ever since then. Again..always on time and on budget. They send a text with a picture of who is coming and when they will arrive. This goes along way for making a little old lady feel secure.
Jay - Roseville, CA
GREAT JOB AS USUAL.
Jose - Roseville, CA
On time! Love the technician tracking tool so I know what time they will arrive. Explained my recommendations throughly, great service!
Dave - Roseville, CA
Great as Always
WILLIAM - Roseville, CA
Arrived on schedule. Wore dust covers on his shoes, was pleasant and professional.
Great service from Chuc
Daniel - Roseville, CA
This is the second time we have used Huft. Great communication leading up to out appointments. Both times our technician was Chuc, he has been professional, clean and good at explaining the repairs. Great overall!
Irina - Roseville, CA
Great Customer service
Brian - Roseville, CA
It was a very pleasant experience and the service was reasonably priced. The technician was very professional and explained everything that needed to be don
Performed AC tune up on a Carrier Split System. Installed Hard start kit to reduce compressor amps draw. Refrigerant level was at 110/40 psig, 7 degrees Subcool and 44 degrees Superheat with an outdoor temp of 60 degrees and indoor temperature at 66 degrees and an 16 degrees temperature drop across the coil. Customer would like to wait a season and check refrigerant again next AC Inspection. All checks are within manufacturers spec and system is operating properly. Will have an Heating inspection left in the Fall.
Preformed ac tuneup on a Lennox system no issues or concerns at this time system is operational
Found bad iharmony zone thermostat. Replaced thermostat. System operations ok at this time.
Found that roof package unit is supported properly and could see no signs of water leaking. Plaster on roof may be cracking due to age and settling of home.
Performed after hours diagnostic on commercial package unit. Found that the belt for blower motor was extremely loose and blower wasnâ€™t spinning fast enough to move proper airflow. Tightened and system cooling now.
Performed ac tune up for Goodman package unit. Tested and checked system in cooling mode. Found no issues. System is operational at this time. Signed up on super hero club membership.
Performed A/C tuneup on a Rheem unit. Found blower motor leaking oil and the shaft is moving in and out of the motor. Recommend replacing. Installed a surge protector for the homeowner. All checks are within manufacture specifications and the system is operational at this time.
Performed ac tune up on Lennox AC. All checks ok. Continue regular maintenance to ensure proper performance and efficiency. Thank you for your business!
Performed furnace tune up on Lennox gas furnace. All checks ok. Thank you for your business.
A/C tuneup completed on a Goodman system. System operations ok at this time. Installed a surge protector on the a/c unit.