for Roseville, CA
Irina - Roseville, CA
Great Customer service
Brian - Roseville, CA
It was a very pleasant experience and the service was reasonably priced. The technician was very professional and explained everything that needed to be don
Replace existing split gas/electric system with a Lennox Energy Star condenser and 80% AFUE furnace. Enlarge return air to 18â€ round and a 20â€ X 25â€ High Flow Grill. Replace all registers and seal register boots to Sheetrock. Replace plenum and adjust collar location for better airflow in the kitchen/family room area. Install Honeywell T6 programable thermostat. Install Healthy Climate 11 filter. Installation includes: HERS Certification with a third party including duct leakage test, labor, permits, taxes and all material. Lennox: ML14XC1-030-230, ML180UH070XE36B, LH24/37X9 AHRI# 201758863 10 Year Parts and Compressor, 20 Year Heat Exchanger, 2 Year Labor, 1 Year Maintenance
Performed a realtor inspection on a carrier system checked furnace first the run capacitor is weak drain pan has no flood prevention switch furnace is operational Check in ac mode system has no hard start kit R22 refrigerant pressures are 62/171 with charging blanket outdoor temp 58 degrees no other issues or concerns at this time ac system is operational Recommendations Superhero club 10mfd run capacitor Flood prevention switch Hard start kit help extend the life of the compressor
Diagnostic preformed on a York system I Remove and replace run capacitor and hot surface igniter signed client on superhero club after repairs checked system, is operational at this time
Found weak capacitor on blower motor
Performed free second opinion on Goodman split system. Found that system is low on refrigerant, but due to weather, it is difficult to properly charge system. Recommend having us back out in April to charge system properly and do leak search. Could not find leak with electronic leak detector.
Carrier furnace was working at time of arrival. Has possible bad gas valve. Told homeowner to call us if it stops working again.
Performed a heater tuneup on a Trane furnace. Found weak capacitor on blower motor and a dirty filter. Informed tenant to replace filter asap.
Performed heating tune up for Lennox spilt system. Tested and checked system in heating mode. Found no issues with system. Changed 20x25x5 merv 11 filter. System is operational at this time.
Performed Heating tune-up and Inspection on a Goodman high efficiency Gas furnace. All safeties check are good and System is operating properly. Renewing Superhero club membership today and will have two more visits.
Performed ahsi. All checks ok. Continue with regular maintenance to ensure proper performance and efficiency. Thank you for your business.