for Rocklin, CA
Quoted new high efficiency heating and air conditioning system.
XC16/EL296- Removed and properly dispose of existing gas/electric split system, provide and install new 4/ton gas/electric split horizontal system in attic, new 1-25x14 & 1-30x20 high flow grille, flushing existing refrigerant lines, new Honeywell zone control with one sensor, ecobee controls, low voltage wiring as needed (rough patch only if requires cutting walls), new merv-13 filter/cabinet/registers, new gas flex connector/shut off valve, new a/c pad, new disconnect/whip, installation includes equipment, material, permit, title 24, third party verification, and taxes. A/c model: XC16-048-230-04 Furnace model: EL296UH090XV60C Coil model: LH49/61W9 SEER: 16.0 EER: 12.5 AFUE: 96%
Preformed furnace tuneup on Goodman system Gas valve is intermittently failing they have replaced gas valve before it Could be control board electrical issue causing issue with gas valve I had to tap it to get it to come on a couple of times during start up I washed a dirty filter No other issues or concerns at this time system is operating with issue client wants to go over replacement options before repairing
Provided new quotes to homeowner- 4.ton gas electric split horizontal in attic. Customer wants name change to multiple pump solutions instead of Fatima patilamo.
Checked heat operations, gas pressure, and temperature split on a Goodman furnace. System is running at manufacture specs.
Quoted new high efficiency furnace and air conditioner.