for Rocklin, CA
Vanessa - Rocklin, CA
Sue - Rocklin, CA
Matt was very professional, took care of the AC problem, explained everything. Very neat , organized . Put everything back after he was done. When I need your service in the future, I will always request Matt.
Steve - Rocklin, CA
Great job! Appreciate your service.
John - Rocklin, CA
Kristin - Rocklin, CA
Great employees at Huft! All of them were very helpful, knowledgeable and professional.
Excellent Customer Services
MARK - Rocklin, CA
Jet came out for a follow-up appointment to check the status of a leak in our system. Although he was not able to find the leak (he said it was most likely inside our walls), he gave us several options on how to best move forward. Jet was very helpful and friendly, and provided excellent customer service.
Excellent company from Gina (scheduler) to Chuc Nguyen (technician).
Mirabelle - Rocklin, CA
I have a really old furnish and Mr Nguyen fixed it in like 5 minutes!! Very professional, informative and most importantly KIND. Thank you so much. May God continue to bless you and your family and Huft Heating & Conditioning.
Dan - Rocklin, CA
He was great! Thank-you very much
Found a bad dual capacitor. Replaced a 70/5 dual capacitor. System operations ok at this time
Performed diagnostic on split York system. Found bad capacitor. Rated 35/5, reading 13/5. Replaced and tested system. Has an 18 deg temp split now.
Quoted new Trane and Lennox split gas/electric.
Remove existing equipment and haul away. Install new Lennox XC16/SL280, 16 SEER AC /80% Furnace. 2 stage heat and cool. Reconnect condensate lines and verify flow to the exterior and add condensate safety switch. Install new electrical dis-connect at condenser with properly sized fuses and weatherized whip. Upgrade existing 3/4 refrigerant line to 7/8 inch. Install new 2 Stage zoneboard and connect to new wi-fi Thermastats. Replace existing servo motors with new Z Tech damper motors. Enlarge attic access for equipment clearance. Remove registers, manually seal boots and install new hi-flow registers. Upgrade to MERV 11 5 inch filter. HERS certification includes third party duct pressure test. Freon recovery per EPA regulations. Installation includes equipment, material, labor, all required testing, rebate processing (when applicable) taxes and permits. Installation total $15,384.00 Rebate - NA Due on completion - $15,384.00
Gave options on Trane 2 Stage with/without zoning.
Installed new whf. Tied in power to a plug from a junction box in attic feeding a bunch of lights. I tied off the constant feed to the box.
Found the capacitor for the fan dead reading 0 mfd. recommend changing capacitor. And recommend membership. Homeowner accepted my recommendation. System is operational at this time.
Used up light did not find any leaks. Used electronic leak detector and found leaks at the schrader core on both high side and low side along with under the service valve caps. Recommend replacing schrader cores and use leak lock on the service caps
Performed a second opinion on a American Standard unit. Found unit low in refrigerant. Possible refrigerant leak. Unit was charged by another company 2 weeks ago.
No cool call for a carrier package unit. All components are operating within manufacturers specifications. I Could not duplicate the issue customer had on Friday. System is operational at this time.