for Rio Linda, CA
Martha - Rio Linda, CA
Upon arrival system hasnâ€™t been turn on since 2012, no information on the system. Upon further inspection, found low voltage wires has been chewed up by rats, drain hoses at the collection box been chewed up as well, blower wheel has built up, duct system is in rough shape. System is NOT in operation at this time. Would like to schedule a comfort advisor for whole central heating and cooling for the home. *Was not able to perform maintenance due to system being in rough shape, did not charge for the visit.
Upon arrival, System keeps shutting off after ignition. Found dirty flame sensor; cleaned flame rod and system ran fine. After shut off system, the Inducer and Blower Motor stays on: Control board is intermittent and malfunctioning and needs to be replaced.