Performed ac tune up Lennox heat pump system. Tested and checked system in cooling mode. Found no issues. Checked all safeties and connections. System is operational at this time.
Emailed different proposals for customer to review. Son will be the main decision maker.
Signed up on Superhero club membership today and performed first visit Heating inspection on a Rheem Split System. High limit keeps trippin; adjusted Gas Pressure, remove dirty filters, adjusted Blower motor speed and system is operating properly. Advised to change filter regularly. Will have one more visit left.
Performed ac tune up for Lennox heat pump system. Tested and checked system in cooling mode. Found no issues. Changed 20x25x5 merv 13 filter. System is operational at this time.
Performed last visit AC tune up on a Lennox Heatpump Package unit. All electrical wires and components are within manufacturers spec, drain lines were cleared out, and refrigerant level is balanced. System is operating properly at this time. Thank you
Got info on UV bulbs and will try and find them and return to replace.
Reconfigured stat wiring and zone control board. Blower motor is hunting even with the tstats off. Will need to order new blower motor and return to replace.
Replaced control board on air handler. Tested system 3 times and indoor fan shut off properly each time.
Found blower motor mount was broken and rubbing up against housing. Remove and replace mount with new mount. Also found filter very dirty, let homeowner know that filter needs to be changed every 30 to 90 days. System is operational at this time.
Continuation of installation of system.