Checked condensate drain line primary drain line was clogged I purge drain line with nitrogen also purge secondary drain line checked drain line outlets both are draining properly at this time told client to keep an eye on the secondary drain line if it doesnâ€™t stop draining to give us a call
With through issues with Dave. Will return today to relocate duct on wrong zone. Install 4 different registers downstairs. Will need to order a oddball 2 way for kitchen area to throw air better.
Performed ac tune up for Amana split system. Checked all safeties and connections. Checked filter. Washed outdoor unit. System is operational at this time.
Quoted multistage Lennox upflow in closet, customer will now talk to wife before making final decision
Signed agreement for Trane proposal
Preformed leak search Found a leak in the Evap coil call Goodman to see if system is still covered under parts warranty, parts warranty has expired
Found leak at 90 joint on primary drain line. Repaired leak. Job covered under warranty.
Perform diagnostic on a York system. Found zone board intermittent, would cause system would not turn on when call for. Tighten all wiring connection and system would work properly while performing diagnostic. If issue occur again, zone board may need to be replaced. Will waive diagnostic fee if repair is made.
Upon arrival homeowner stated the ac unit isnâ€™t working. Upon investigating I found a bad capacitor. Replaced the capacitor and tested the system. The compressor still wouldnâ€™t come on. Checked the contactor and all wires. And they are good. Determined the compressor is bad also and will need to be replaced.
Gave options on Lennox and Trane 2 Stage equipment.