Found dirty filter on carrier air handler. Also inspected to find cause of different air temperature in each room. My only explanation would be the way the supply plenum is designed. Homeowner will replace filter.
Set appointment for comfort advisor. No charge.
Performed Annual Heating Safety Inspection on a Coleman rooftop Heat pump. All safeties check are within manufacturers spec and system is operating properly. Also check water heater noises; cleaned and show h/o how to washed filter, cleared drain lines and unit is operating properly.
Replace outdoor txv and filter dryer on package heat pump, has part warranty form the manufacturer
Performed furnace tuneup on a Goodman furnace. Found no issues at this time. All checks are within manufacture specifications. System is operational at this time.
Checked a rheem system for A noise complaint upon arrival turn system on could not get noise to reoccur checked system did not see anything unusual told client to try and record it next time and give us a call system is operational at this time
Performed heater tune up. Recommend renewing super hero club. All checks ok.
Went over hot water tank issue. Found that master bathroom shower may be issue. Turned off water inlet valve at tank and still was having water leaking out of hot water side continuously. Master shower doesnâ€™t heat up as much as other fixtures. Has issue with cold water bypass recommend calling Boyd plumbing to investigate issue further.
Performed heating tune up for Lennox spilt system. Tested and checked system in heating mode. Found no issues. Changed 20x20x5 merv 11 filter. System is operational at this time.
Performed furnace tuneup on a Coleman furnace. All checks are within manufacture specifications. System is operational at this time.