for Rescue, CA
Marty - Rescue, CA
Very personable great experience
James - Rescue, CA
Took window measurements to do load calc, but could not get into home to look at ductwork and insulation to do properly. Sent options for gas/electric package units. Uses propane. Would like to look at ductwork and return size when possible. Call with any questions.
Found package unit running ok for age at 24 years old. Found the low voltage control wire for power had no insulation on it for about 8â€. Taped it up so it doesnâ€™t cause a short. Blower wheel is a little dirty but not bad. Capacitor for compressor and outdoor fan at minimum specs. Split Trane unit is running ok. Could not see any cracks on heat exchanger. Recommend exploring replacement options on package at least due to age and R22 refrigerant.
Installed an iwave that homeowner won from the home show.