for Orangevale, CA
Phong Tran Technician
Scott - Orangevale, CA
Matt - Orangevale, CA
Mike - Orangevale, CA
Shun did a great job, on time, polite, clean
Promt and curteous service
TONY - Orangevale, CA
Signed up on Superhero club membership and performed first visit A/C tune up on a Lennox system. System was low on refrigerant, added 4.1 lbs of 410a refrigerant to get to proper level. Inspect for leaks but none were detected at this time, injected uv dye to reschedule in two weeks for leak search. Compressor start up amps draw was pulling max amps and drain pan has no flood safety switch. All electrical wires and components, condensation drain lines, filter and outdoor coil is washed clean.
Quoted new Lennox High Efficiency Variable Capacity Heat Pump.
Found bad dual run capacitor. Replaced dual run 40/7.5 cap. Found system low on charge, customer wants to have customer advisor to come and talk about new system.
Found leak at copper at suction line connections near air handler. Repaired leak. Repaired inspections corrections on heat pump water heater. Tested Hvac systems, system is operating properly at this time.
Conducted heating tune up on Goodman furnace. All heating safety switches and components are operating within manufacturers specifications. Performed air conditioning tuneup on unknown brand with missing data plate. I put all my measured data in as a reference point. The duct work running to the back bedroom is putting low airflow out. Recommend adding Manuel dampers. Or complete rebuild of air duct system. System is operational at this time.
Performed air conditioning tuneup on a Rheem package Unit. Found the dual capacitor under manufacturers specifications. The capacitor is rated at 45/5 mfd. recommend replacing dual capacitor. Replaced dual capacitor. System is operational at this time.
Went over final inspection paperwork and set appt for tues 6/16 for inspection. Found loose wire for ceiling fan in bedroom. Redid wiring and tested. Need to return to do leak search and touch up paint on ceiling in guest room.
Performed ac tune up for Nordine spilt system. Checked all safeties and connections. Checked filter. Disassembled and cleaned blower motor and blower motor Housing. Washed outdoor unit. System is operational at this time.
Preformed ac tuneup on a Rheem package unit system has no hard start kit, surge protector no other issues or concerns at this time system is operational
Found system low on r410a and the filter was extremely dirty Charged system to manufacture specs replaced filter I added dye to the system tech need to check for leak doing heater visit