for Mather, CA
FRANK - Mather, CA
I am happy with the company.
Added 8â€ damper to supply into master bedroom. Throttled airflow back quite a bit, customer said he thought it felt better. He also asked to not install dampers in the other ducts. Re-ran return flex duct, removed approx. 30â€ and tightened run up. Repaired primary condensate fitting on platform Removed trash
Preformed diag. on a Carrier system upon arrival client said unit was not cooling the house properly I checked AC unit The filter needs to be changed system has no hard start kit no other issues or concerns at this time system is operational
Performed annual AC inspection and tune up on Trane split system. System is operating properly at this time.
Customer is saying that the master bedroom is getting to cold and rest of home not cooling as well. Has dedicated 8â€ duct to master on top of plenum towards back. Need to return to install a 8â€, a 5â€, and a 4â€ manual dampers. Also may need to redo return duct.
Performed AC inspection and tune up on Carrier split system. Customer informed technician that the downstairs thermostat was not working. System is zoned for upstairs and downstairs. Recommend replacing the downstairs thermostat. Found the blower door was a bit loose and when moved slightly, it would open the door safety switch and the system would shut off. Secured blower door and verified it was not loose anymore. Cleaned outdoor condenser coil. System is operating properly at this time. Customer signed up for superhero club membership. Today is the first visit. One visit left.
Found bad capacitor on carrier condenser. Replaced capacitor and added hardstart kit. Tested system for proper operation. System is operational at this time.
Install Bosch 2/3 ton Variable capacity heatpump. Haul away old equipment. Install new supply plenum to improve airflow. 3rd party HERStest included. Installation includes equipment, materials, labor,permits and rebate processing. Taxes included. Installation total $12,431.00 Rebate. ($4000.00) signed over to Huft Amount due $8431.00
Went over replacement options for heating ac system
Performed Air conditioning tune up on York system. Found system low on R22 refrigerant. Filled system with refrigerant. All checks within specifications and maintenances performed.
Performed sidekick club maintenance tuneup. Tested and checked system in heating and cooling mode. Found no issues. System is operational at this time.