for Lodi, CA
Sheryl - Lodi, CA
Larry was a breathe of fresh air...honest,professional, and thorough in his assessment of our issue. I can’t thank Huft enough for hiring great people.
Great tech, great service!
Dustin - Lodi, CA
jason - Lodi, CA
Awesome he was very informative
Praneet - Lodi, CA
Jim - Lodi, CA
Review for Larry Goerzen
DAVID - Lodi, CA
Tami - Lodi, CA
JENNIFER - Lodi, CA
I received a call letting me know he was on his way and he arrived on time and got straight to work. His name was Larry Goerzen. He was super polite and very nice.
Raymond - Lodi, CA
DENNIS - Lodi, CA
Looked at duct work and gave a quote for new duct work to be up to code.
Performed a tuneup on ruud ac system. The compressor LRA are just abouve manufacture specifications at 64.4 and manufacture recommends 64 or below. All other checks are within manufacture specifications and the system is operational at this time.
Performed ac tune up for Amana split system. Checked all safeties and connections. Changed 14x25x1 filters. Washed outdoor unit. System is operational at this time.
Found blower wheel motor dirty on Trane package unit. Cleaned blower wheel. System is operational at this time
Upon arrival found duct work with holes in it. Rodents had chewed the duct system and recommend replacing all the duct work. 79 dollars diagnostic fee waived its duct work replacement.
Performed ac tuneup. All checks are within manufacture specifications and the system is operational at this time with a 20 deg temp split. Recommend installing hard start kit
LENNOX- Removed and properly dispose of existing gas/electric unit, provide and install new 5.ton multi-stage gas/electric system in attic, flushing existing refrigerant lines, connecting to existing ducting, high flow intakes grilles, healthy climate merv-16 filter cabinet/registers, eco/bee smart thermostat, a/c pad, disconnect/whip, gas flex connector/shut off valve, installation includes equipment, material, permit, title 24, Rebate processing, third party verification and taxes. Includes installation guarantees/warranty. NOTE: Enlarging one of the return to 30x20 if required by new furnace/not fitting into existing attic access. XC16-060-230 2 Stage Air Conditioner SL280UH080NV60- 2 Stage Ultra Low Nox Furnace ADP Coil M# LC42/62W9 Smart Thermostat of Choice Healthy Climate MERV 16 Filter 16 SEER/80% AFUE (AHRI# 202095474) Two stage heating and cooling improves comfort, saves energy, and provides quieter operation. 10 Year Parts/10 Years Labor 20 Year Heat Exchanger 2 Year S
Upon arrival found a Bryant ac unit not operational. Found the condenser fan not working. Upon further investigation I found a bad capacitor. Replaced the capacitor and tested the unit. The system is operational at this time.
Charge a carrier ac system with 5 pounds of r22. Injected leak search dye. Will need to return in two weeks for leak search. Found one schrader core leaking. Replaced the high side schrader core. Tested system and it is operational at this time. System has a 20 degree split.
No quote// will research for a downflow low nox furnace and email proposal to customer. Christopher will be calling carrier/rep to get pricing.