for Lincoln, CA
Great service, awesome
Nick - Lincoln, CA
He was awesome, very informative and just all around great person!
Brian - Lincoln, CA
Shun was very knowledgeable, great job in communication.
Not very happy with communication
Shana - Lincoln, CA
Chad - Lincoln, CA
Adam - Lincoln, CA
The technician that came to my house was great. Virtuous and didn’t push any sales on me. I was referred by RAD radio and I can see why HUFT partners with RAD. Excellent job!
TORI - Lincoln, CA
Matt from Huft has been to our house twice now and both times was great - experienced, professional, on time. Nothing bad to say. The Huft quote is better priced than most we have had, backed by their guarantees.
Susan - Lincoln, CA
Efficient and personable. Answered all my questions in a way I could understand.
Wayne - Lincoln, CA
Chuc figured out the part he was sent to replace wasn’t the cause of the issue, he got the heat working before the root cause could be remedied.
Heat and air repairs and service
Chad - Lincoln, CA
Chuc was great and easy to talk too
Performed air conditioning tuneup on a Goodman condenser with Lennox furnace. The dual capacitor is under manufacturers specifications. The refrigerant charge is higher than manufacturers recommendation. Recommend replacing capacitor and adding a hardstart kit. All other checks and components operating within manufacturers specifications. System is operational at this time.
Preformed furnace/ac tuneup system has no flood switch and no hard start kit I added a flood switch no other issues or concerns at this time system is operational
Performed air conditioning tuneup on a York split system. Found all components and checks within manufacturers specifications. System has a hardstart kit on it. Changed 20x30x1 air filter for the home owner. Washed the condenser coil. System is operational at this time. Recommend superhero club renewal.
I met with the husband Tom. He will go over it with Kristen when she gets home from work.
Found York split system not working. Opened electrical panel and saw the dual capacitor was missing. And a hard start kit was installed. The compressor and fan wires were hanging freely in the panel. I tried adding a dual capacitor and found the compressor short cycling. I investigated the compressor wires and saw that the wire for the run cap was corroded and broken off from compressor.I recommend seeking replacement option.
Found system low on refrigerant R-22, high amp draw on start up measured at 135 rated at 165. Recommended recharge and a hard start kit. Homeowner wanted a comfort advisor to visit for estimate on new system. Appointment set for June 3 2020 at 1 pm.
Customer wants to reschedule.
Found bad dual run capacitor. Replaced a dual capacitor. System operations ok at this.
Preformed ac tuneup on a York system there is no hard start kit no other issues or concerns at this time system is operational
Performed ac tune up Goodman spilt system. Tested and checked system in cooling mode. Checked all safeties and connections. Checked filter. Washed outdoor unit. Added 2.5 lbs of refrigerant to system. Also installed a hard start kit to outdoor unit. System is operational at this time. Signed up on super hero club membership and performed first visit today.