for Lincoln, CA
Susan - Lincoln, CA
Efficient and personable. Answered all my questions in a way I could understand.
Wayne - Lincoln, CA
Chuc figured out the part he was sent to replace wasn’t the cause of the issue, he got the heat working before the root cause could be remedied.
Heat and air repairs and service
Chad - Lincoln, CA
Chuc was great and easy to talk too
Performed annual AC inspection and tune up on Lennox split system. Replaced filter today. Cleaned outdoor condenser coil. System is operating properly at this time.
Blower capacitor needs to be replaced. Reading 4.2 mfd, rated 5 mfd. hardstart kit recommended. Compressor start up amps rated at 60A, reading 58.2A. System isnâ€™t running bad for 17 years.
Emailed proposal to customer for reviewed
A/C tuneup completed. System operations ok at this time. Renewed super hero club. Has a heat tuneup left.
Found control board miswired. Rewired control board and set dip switches for proper operations. System operations ok at this time.
Installed new Quiet Cool Whole House Fan.
Sold a Quiet Cool 4.8 STL PRO and running a dedicated line from the breaker box. Homeowner will call office to have it scheduled.
Performed diagnostic. Found seized inducer motor. Replaced inducer motor. Ran tested for 30 minutes prior to departure. Recommend super hero maintenance club.
Performed heating and cooling tune up for Lennox spilt system. Tested and checked system in heating and cooling mode. Found no issues. Washed filter. System is operational at this time.
Performed a heater tuneup on a York furnace. Found weak blower capacitor and hot surface igniter reading high resistance. Replaced a blower capacitor and igniter. Also repair a duct and installed a Nest thermostat. Signed up for super hero club. Has an a/c tuneup left. System operations ok at this time.