for Ione, CA
Performed system tuneup on Lennox package unit. Checked disposable filter and replaced today. Checked system for proper operation. System is operational at this time.
Found system low on refrigerant and not cooling house properly. Recommend adding refrigerant to system to manufacturer specs and performing a leak search on system. Homeowners want to hold on repairs for now.
Performed a tuneup on Goodman furnace and ac. All checks are within manufacture specifications and the system is operational at this time.
Remove bad blower motor and replace with new. Tested system. Performed one time AC tune up on both systems. Systems performing ok now.
Performed a tuneup on a Payne ac unit. Recommend a blower wheel cleaning and replacing blower motor. The blower motor bearings are going out. All other checks are within manufacture specifications and the system is operational at this time.
Performed diagnostic on split Payne heat pump. Found blower motor bad. Has 24V to motor but wont run. Will have to order in morning. Will want to do acsi on 2 systems when we return to do motor repair.
Performed a tuneup on a ameristar ac system. All checks are within manufacture specifications and the system is operational at this time
Goodman â€” Removed and properly dispose of existing rooftop unit, provide and install new 3.ton goodman single stage gas/electric rooftop system, new curb/drop, connecting to existing ducting, discontinuing supply feeding garage, new 25x20 high flow grille, merv-13 filter/registers, new t-6 Honeywell thermostat, new gas flex connector/shut of valve, new disconnect/whip, installation includes equipment, material, crane, permit, title 24, third party verification and taxes. Install date: 3-30-2020 Completion date: 3-30-2020
Customer purchased new 3.0ton gas/electric rooftop package system to be install on Monday march 30, 2020
Quoted for a 2.0ton gas-electric rooftop Lennox