for Gold River, CA
Terry/Roxann - Gold River, CA
Chuc was great! He explained everything he was doing . I didn’t have any additional questions or concerns. Great job!
Nicholas - Gold River, CA
Chuc was very professional
Performed air conditioning tune up on both Lennox systems. Found LRA to be higher then manufacturer specifications on both system. Installed hard start kit for both systems. All other checks are within specifications and maintenances performed.
Replaced control board on a Rheem hp water heater. Also completed all corrections. System operations ok at this time
Dropped off inspection papers and set appt for Friday.
Performed acsi on 2 ac units. All checks ok. Recommend continuing regular maintenance to ensure proper performance and efficiency.
Replaced upper and lower sensor for heat pump water heater. Tested and system working now.
Performed heating tune up for Goodman furnace. Tested and checked system in heating mode. Found no issues. System is operational at this time.
Performed heating tune up for both Lennox systems. Tested and checked systems in heating mode. Found no issues. Systems is operational at this time.
Performed heating tune up on Day and Night split system. Will replace MERV 16 20x25x5 filter at next visit.
Inspected in siding of home. Could not see any reason that the ac/furnace systems are the cause of issue. Could see no leaks from condensate lines or over flow lines going into wall. Cannot see in wall if the condensate line was leaking without taking off siding.
Found a bad zone board on a York furnace. Homeowner will talk to his wife to see if they want it replaced.