for Galt, CA
WILLIAM - Galt, CA
Great service from this tech always!!
GAIL - Galt, CA
SCOTT - Galt, CA
Larry was on time, friendly, professional and was speedy in diagnosing and repairing the problem with our air conditioner! I would definitely recommend Huft Heating & Air!
Very Nice to Deal With
DAVID - Galt, CA
The technician was prompt, courteous and meticulously neat. I was called in advance and he treated my home with great care. During the era of covid, he wore a mask and gloves even while working in my attic during a brutally hot day. The service was performed promptly and according to the quoted price.
Dustin - Galt, CA
Andre was very nice and helpful.
Great service, Larry is a wonderful employee.
SUZIE - Galt, CA
It’s nice having a knowledgeable person explain the problem in simple terms.
Good honest service
Jeff - Galt, CA
Larry was an excellent technician. He was quick to diagnose and find the problem with our ac, and very informative about what our options would be to fix it. 10/10 completely satisfied!
Always great service
WILLIAM - Galt, CA
Phong is very dedicated and knowledgeable.
Very helpful and accommodating with our needs and wants
Steve - Galt, CA
Anthony - Galt, CA
Matt was very friendly and informative. He explained the situation I was in with my unit and gave me options to think about. He was honest and straight forward.
Upon arrival homeowner stated the Rheem ac unit isnâ€™t cooling. Upon investigating I found the system flat on refrigerant. Recommend adding 5 pounds of R410A and UV dye. Then we would need to return in two weeks to perform the leak search.
Warranty coil install. Remove old coil. Install new aspen coil. Pressure test system, vacuum system to get all impurities out then charge system to manufacturers specifications.
3 Ton 14XC1 & ML180E Horizontal Replace existing split system with a Lennox Single Stage split system with Energy Star Condenser. Install Honeywell T6 Pro thermostat. Move condenser just around the corner from existing location. Increase the Return Air to a 18â€ R-8 Silver Jacketed duct and keep the grill size the same 30â€ X 20â€. Replace the ductboard plenum with a 26 gauge metal plenum. Replace 50 gallon gas water heater with a Rheem 50 Gallon gas water heater. Installation includes: Installation by HUFT Journeyman employees, Ceiling saver condensate pan, all Comfort Guarantees, secondary overflow safety switch, remove and dispose of existing equipment, Title 24 HERS certification with a third party including duct leakage test, gas flex with ball type shut off valve, electrical disconnect with properly sized fuses, perform line set flush, dispose of existing equipment, weather tight flexible whip at condenser, new high flow return air grill, Healthy Climate 11 filter, sea
Performed leak search and found leaks at the Evaporator coil, no leaks were detected elsewhere. Ordered coil on will call at Goodman Bradshaw. Also check refrigerant level and have to add one pound under warranty to system spec. Will have to reschedule to replace coil.
Lennox - Removed and properly dispose of existing gas/electric unit, provide and install new 3.ton multi stage gas/electric system replacement horizontal in attic, enlarge intake to 30x20 with 18â€™ return duct/high flow grille, healthy climate merv-13 filter cabinet/registers, flushing existing refrigerant/drain lines, connecting to existing ducting, gas flex connector/shut off valve, Emergency pan with flood protection device, new pvc flue pipe, a/c pad, new Lennox E-30 smart thermostat, disconnect/whip, Replace existing natural water heater with new Rheem 50 gallon natural gas water heater. Includes new gas shut off and flex line, new water lines, expansion tank, flexible water lines, earthquake straps, installation includes equipment, material, permit, title 24, third party verification, rebate processing and taxes. Note: Daughter (Tracy) will be present on Friday 6-26-2020 to go over new system. HEATING AND AIR SYSTEM: M-#XC16-036-230-05 M-#EL296UH070XV36B M-#LH23/37W9 XC16- 2
Performed a leak search and found a leak on the evap coil. Need to reschedule when part comes in.
Preformed ac tuneup no issues or concerns system is operational at this time
Diagnostic performed upon arrival condenser fan was not turning i check the dual run capacitor, had failed I replace capacitor test system is operational at this time Recommended superhero club
Return to install a new contacter. Tested the system several times and it is operational at this time.
Performed tuneup on a a ac and heater package unit. Data plate has been removed so unable tell model. All checks are within manufacture specifications and the system is operational at this time