for Folsom, CA
JOHN - Folsom, CA
Chuc has been sent before to service or troubleshoot a problem. He’s always been friendly, courteous and knowledgeable. We had a bad thermostat so he went to the distributor returning within a half hour with a new one, problem solved
Charlotte - Folsom, CA
Completely confident in everything that needs to be addressed. Also comfortable with having him in my home. ( did all his computer work at the itty bitty kids table while I was getting my 2 year old bathed and ready for bed) we had a 5 to 7 pm appointment. So dinner and crazy was all part of this appointment. Gave me all the information so I could have that conversation with my husband when he got home from work. Best part is that he got the issue fixed temporarily so at least we have heat. Thank you so much!
MIKE - Folsom, CA
Fantastic! Good honest guy
Performed diagnostic on Lennox split heat pump system. System is performing well now with a 24 degree temp split. Temperature went up in home 3 degrees in 1/2 hour. Adjusted some settings in system.
Found zone 2 damper motor not working. Will have to ordered parts and reschedule for repair.
Found bad zone stat on a Lennox unit. Picked up a new zone stat from Lennox and replace part. System operations ok at this time.
Went over financing options for repair.
Performed Annual Heating tune up and Inspection. System is operating properly and safely. Replaced the 20x25x5 filter. Customer is due for renewal, club membership denied at this time.
Performed diagnostic on 19 year old Goodman package unit on roof. Found blower motor sticking. Able to get it working, but may fail again. Kicking out on high heat which may be due to blower motor not moving air as fast as it should and blower wheel being very dirty. Recommend exploring replacement options, due to age and condition of system.
Found alert for pure on S30 thermostat saying filter at 70% and the purifier at 30%. Will check next week about changing out filter. System ok to run now. Filter was a little loaded with dust and dirt.
Performed a tuneup on a York furnace. Checked heat operations, all components, and safeties. System ops ok at this time.
Found bad dual capacitor on a Bryant a/c unit. Replaced dual capacitor. System operations ok at this time.
Performed heating tune up for York split system. Tested and checked system in heating mode. Found no issues with system. System is operational at this time. Signed up on super hero club membership.