for Folsom, CA
JEFF - Folsom, CA
Good service with knowledgeable people. Very pleased with service from Andre.
STEVE - Folsom, CA
Cindy - Folsom, CA
Great work and quick
LISA - Folsom, CA
Shun was excellent; on time, professional, and quick.
Customer satisfaction survey
Natalie - Folsom, CA
George - Folsom, CA
Shun came to our home to perform a routine maintenance as well as to look into an error code that had appeared on our thermostat. He was clearly well versed in his knowledge of the system as he explained what the problem was, or in this case, what the problem wasn’t. He then went on to conduct the maintenance in a professional and efficient manner. And he has such a friendly disposition too! Thank you, Shun!
ALEX - Folsom, CA
Alex, Kenneth and Trever were an awesome team who installed our new HVAC system in a quick and efficient manner. They were quick to answer any questions we had and left no trace after they finished. One of the best experiences my wife and I have had in the area of home improvement/repair.
Great experience all around
JENNI - Folsom, CA
JOHN - Folsom, CA
Chuc has been sent before to service or troubleshoot a problem. He’s always been friendly, courteous and knowledgeable. We had a bad thermostat so he went to the distributor returning within a half hour with a new one, problem solved
Charlotte - Folsom, CA
Completely confident in everything that needs to be addressed. Also comfortable with having him in my home. ( did all his computer work at the itty bitty kids table while I was getting my 2 year old bathed and ready for bed) we had a 5 to 7 pm appointment. So dinner and crazy was all part of this appointment. Gave me all the information so I could have that conversation with my husband when he got home from work. Best part is that he got the issue fixed temporarily so at least we have heat. Thank you so much!
Performed ac tune up for Lennox spilt system. Tested and checked system in cooling mode. Found no issues. Checked all safeties and connections. System is operational at this time. Installed hard start kit to outdoor unit.
Replaced PCO3-20-16 pure air kit. Kit includes MERV 16 filter, UV bulb, and photocatalytic cartridge. Replaced for no charge as part of the new install.
Performed annual AC inspection and tune up on Lennox split system. Noticed pure air information on the S30 thermostat reading Filter at 60% and purifier at 20%. Set up a visit to replace the filter for no charge on March 23rd. System is operating properly at this time.
Found clogged drain trap on furnace and flame sensor with a low micro amp reading of 2.5 even after cleaning it. Need to order part and reschedule
Diagnostic performed found a bad hot surface igniter replaced igniter tested system ran for about 30 minutes system did not pop breaker system is operational
Rewired system from previous tech. Wired up tstats as conventional gas heat to zone board. Set up zone board to recognize equipment as heat pump, but thermostats as conventional. System working in ac and heat now.
Found low voltage wire not hooked up in the correct terminal on the thermostat. Rewired low voltage and cycled system. System operations ok at this time.
Performed real estate inspection. All checks ok. Recommend super hero club maintenance to ensure proper performance and efficiency. Thank you for your business, congrats on the new house!
Performed acsi. All checks ok. Recommend super hero club maintenance to ensure proper performance and efficiency
Preformed AC tuneup on a Lennox heat pump system no issues or concerns at this time system is operational