for Fair Oaks, CA
We really liked Shawn! !
ANDREA - Fair Oaks, CA
Liked that he looks straight at you which is telling us he has confidence.
Chuc did just fine
Greg - Fair Oaks, CA
Quick, Friendly & Professional
Lindsey - Fair Oaks, CA
Ryan did a great job quickly diagnosing the problem and fixing it. He was very knowledgeable and genuinely cared about getting our unit fixed. He’s a true pro!
Sharon - Fair Oaks, CA
Lindsay - Fair Oaks, CA
Phong was great. He was thorough and explained everything in detail. He and his partner were very respectful, professional and courteous. It was a great experience all around.
Went over duct and insulation replacement options.
Performed diagnostic on split Lennox system. Found that system was throwing error code for loss of power to inverter board for more than 3 minutes. Did a hard reset and system performing well now. Probably from when we replaced disconnect. Tested in AC
Remove existing wall furnace and window air conditioner and install a Lennox Ductless Mini-Split system with a 3 ton Heat Pump and three 3/4 ton heads for the bedrooms and a 1 1/2 ton head for the main living area. Run a 220V circuit to the heat pump. Run line sets and condensate drains to each head. Installation includes: All material, taxes, labor and rebate processing. Lennox: MPB036S4M, MWMA009S4-3P (3 Each for bedrooms and man cave) MWMA018S4-3P 7 Year Compressor, 5 Year Parts, 2 Year Labor Project Cost: $13,802 SMUD Rebate: -$4,000 Paid to Huft: $9,802. ($113.76 Monthly for 120 Months or 18 Months Same as Cash) Lennox Rebate: -$600 NET INVESTMENT: $9,202
Looked at noise on outside flue. May be from such a short flue at only about 4 feet. Needs to have Clark and rush out to diagnose. If we work on it could void any labor warranty.
Performed cooling maintenance on split Amana system.
Quoted new Ductless Mini-Split Heat Pump System.
Preformed sidekick furnace and ac tuneup unit has no air cleaning system no other issues or concerns at this time system is operational
Performed Annual AC tune up and Inspection on Trane Package unit. Cleaned washable filter and condenser coil. All checks are within manufacturers spec and System is operating and cooling properly. Renewing Superhero club membership today and will have two more visits left. Thank you for your business.
Preformed Realtor inspection I checked the furnace first no issues or concerns with Operation of the furnace I noticed that the system does not have a flood prevention switch and also the blower wheel needs to be cleaned system Has the old-style black flex duct Checked the system in AC mode R22 pressure are 55/195 with charging blankets Outdoor temp 58 degrees the dual run capacitor is very weak system has no hard start kit it will help extend the life of the compressor Recommendations Superhero club membership (You will receive 10% discount) Blower wheel cleaning Flood switch/pureairx Dual run capacitor Hard start kit