for Elk Grove, CA
RS - Elk Grove, CA
Prompt, honest, quick, friendly.
Jimmy - Elk Grove, CA
I was floored at the extent the technician went to for such a low payment. He went way above and beyond.
Yvonne - Elk Grove, CA
Real pro. Thanks for sending him
Sheryl - Elk Grove, CA
Once again Huft did not disappoint us Matt was here in less than half an hour did a great job and totally resolved our issue. Thank you for the great people 🤗
Fantastic customer service
Jacqueline - Elk Grove, CA
Paul - Elk Grove, CA
AC went down in July, Larry was able to accommodate us early and got us up and running quickly. Was completely transparent and demonstrated the problem to us. Larry was polite and professional would highly recommend!
Very fast service, great employee
Andrea - Elk Grove, CA
ROMEO - Elk Grove, CA
Frank - Elk Grove, CA
Phong, services was really appealing!
Sukh - Elk Grove, CA
The service was great. Chris was very informative and helpful.
Quoted multistage Lennox upflow in closet, customer will now talk to wife before making final decision
Signed agreement for Trane proposal
Preformed leak search Found a leak in the Evap coil call Goodman to see if system is still covered under parts warranty, parts warranty has expired
Found leak at 90 joint on primary drain line. Repaired leak. Job covered under warranty.
Perform diagnostic on a York system. Found zone board intermittent, would cause system would not turn on when call for. Tighten all wiring connection and system would work properly while performing diagnostic. If issue occur again, zone board may need to be replaced. Will waive diagnostic fee if repair is made.
Upon arrival homeowner stated the ac unit isnâ€™t working. Upon investigating I found a bad capacitor. Replaced the capacitor and tested the system. The compressor still wouldnâ€™t come on. Checked the contactor and all wires. And they are good. Determined the compressor is bad also and will need to be replaced.
Gave options on Lennox and Trane 2 Stage equipment.
Diagnostic call on an Amana system that is not blowing cool air. Found burnt Contactor, burnt wires, and weak dual capacitor. Recheck hard start kit previously installed by us, Hard Start are still within spec. Repaired high voltage wiring, replaced new Contactor and installed new Dual Capacitor. System is currently operational at this time. Amps draw were pulling on the higher end of spec, advised customer that system is not efficiently operating due to itâ€™s age.
Coleman - Removed and properly dispose of existing gas/electric unit, provide and install new 3.ton inverted driven 5-stages heat pump split conversion horizontal in attic, 25x20 high flow intake grille, healthy climate merv-13 filter cabinet/registers, new metal/insulated supply plenum, QCTRIPRO3.3X, run new 220v electrical circuit from main panel to attic, Emergency pan with flood safety protection, a/c pad, disconnects/whips, eco/bee smart thermostat, flushing existing refrigerant/drains lines, connecting to existing refrigerant/drains lines, connecting to existing ducting, installation includes equipment, material, permit, title 24, third party verification, rebate processing, and taxes. NOTE: TEMPORARY REPAIRED A/C FOR CUSTOMER. M#CH16B3621S M#AE36BX21 CH16 5 Stage inverter driven heat pump AE Air Handler with ECM Blower motor Smart Thermostat of choice MERV 13 Filter 16 SEER/10 HSPF/ AHRI (#9006275) 10 Years parts/ 10 Years labor 10 Years compressor 2 years side kick clu
Found bad control board. Ordering part from Lennox.