for Elk Grove, CA
Excellent service in difficult times
LINDA - Elk Grove, CA
Thanks to Shun & Matthew for not giving up on a difficult problem to solve in very difficult times! I worried that I would not get help with my new HVAC system during the COVID19 epidemic, but you all came thru—including the office staff. Thank you so much!
Sarita - Elk Grove, CA
Andre was amazing and helped to fix our loud system. Huft is always our first choice.
GAYLE - Elk Grove, CA
Chris was courteous, neat, and explained what he would be doing before he started.
A/C and Heater check up
AMY - Elk Grove, CA
Technician showed up in window of time, also called to let me know he was on the way. Very thorough check up and kept me informed as he was working
PETE - Elk Grove, CA
They were always very professional at what they do.
Reset timer for service to 1 year
Barbara - Elk Grove, CA
MARC - Elk Grove, CA
We have been with Huft for 15+ years and really love them. Jet comes to us the most and he is one of the best, but we don't mind anyone that they send us. 🙂
Technician friendly and respectful
CIDALIA - Elk Grove, CA
Don - Elk Grove, CA
Chuck did a great job. Polite and knowledgeable. I would recommend him to anyone and would request him back for work in the future
ELMER - Elk Grove, CA
Replaced control board on air handler. Tested system 3 times and indoor fan shut off properly each time.
Found blower motor mount was broken and rubbing up against housing. Remove and replace mount with new mount. Also found filter very dirty, let homeowner know that filter needs to be changed every 30 to 90 days. System is operational at this time.
Continuation of installation of system.
Could find no issues with system. Had error code for low pressure switch lockout. Reset system and tested pressures. Ran in heat for 20 minutes with no issues. Pressures at 460/124 with 60 deg ambient. Tested in cooling with no issues. Put back into heat and ran it for another 15 minutes and still no issues. System is running fine now. Call if t happens again.
Dropped off filter by front door
Performed sidekick club maintenance. Tested and checked system in heating and cooling mode. Found no issues. Checked all safeties and connections. System is operational at this time. Signed up on sidekick club membership.
Performed ac tune up for Lennox spilt system. Tested and checked system in cooling mode. Found outdoor unit capacitor was weak. Replaced capacitor with new one. Changed 16x25x5 merv 13 filter. Washed other filter. System is operational at this time. Signed up on super hero club membership.
Found that the ceiling has water damage due to a joint not being properly glued on condensate line. Glued up and checked other joints. Found one other at trap not glued well. Will get back to customer with repairing ceiling.
Bosch 2.0 4/5 Ton Replace existing split gas/electric system with a Bosch 2.0 High Efficiency Variable Capacity heat pump system. Install Bosch BBC100 Wi-Fi Smart thermostat. Zone home with the Honeywell zoning and put second thermostat in the master bedroom. Add an additional 8â€ round R-8 Silver-jacketed supply air to the master bedroom with a 14â€ X 6â€ register. Add a 12â€ round R-8 Silver jacketed return air to a 14â€ X 14â€ high flow grill. Replace other return air grill with a High Flow Grill. Remove and dispose of existing equipment. Installation includes: Title 24 HERS certification with a third party including duct leakage testing, all Comfort Guarantees, new fused disconnect with weather tight whip, line set flush with RX-11, overflow safety switch at secondary condensate drain, all material, labor, taxes, permits and rebate processing. Replace existing gas water heater with a Rheem Hybrid Heat Pump water heater. Bosch: BOVA-60HDN1-M20G, BVA-60WN1-M20 AHRI#
Performed ac tune for Goodman split system. Tested and checked system in cooling mode. Found no issues. Added a flood prevention switch to drain pan. Washed outdoor unit. System is operational at this time.