for Citrus Heights, CA
KARINA - Citrus Heights, CA
Responsive, prompt, and professional. Huft continues to impress with their expertise and superior customer service.
Semi Annual Check Up
JOE - Citrus Heights, CA
Shuntavious Oliver was very thorough, courteous, and helpful in all aspects. We truly appreciate the service!
Found blown t-stat cause by electrical surge. Replaced and ran tested. Waited for Sun Run to call to pay for damage. Tag not paid.
Tested Colman heat pump system. System is operational at this time. No issues were found at this time.
Performed heating tune up for Coleman heat pump system. Tested and checked system in heating mode. Found no issues. Changed 20x20x5 merv 11. System is operational at this time.
Performed heating tune up on Trane split system.
Preformed furnace tuneup on a amana unit inducer motor is making a noise but not over amping no other issues or concerns at this time system is operational
Quoted heat pump split energy star system, Customer will get other bids before making final decision.
Performed Heating tune-up. System was low on refrigerant; performed leak search and found leaks at the Evaporator coil and at the distribution lines on the outdoor coil; suggest both coil replacement. System is currently low on refrigerant at this time.
Performed tune up on Lennox heat pump package unit on rooftop. All checks ok. System is operational at this time.
Preformed realtor inspection on a heat pump trane system filter needs to be replaced I checked the system in heating mode first no issues or concerns with the Airhandler the outdoor unit fan motor is leaking oil but not over amping Outdoor unit was freezing up Iâ€™ve Bang on the TXV Pressures went up to 100/289 but did not fix the problem system started freezing up again TXV has failed r410a pressure 76/289 in heating mode outdoor temp 56 Contactor is burnt and pitted system has no hard start kit and no surge protection Tested unit in AC mode ac Uses the same components as the heater r410a pressure 110/289 in ac mode Recommendations Superhero club membership replace outdoor TXV Replace contactor Replace outdoor fan motor with ecm fan motor 1/6 Add hard start kit to help extend life of the compressor Add surge protection
Preformed ahsi no issues or concerns at this time system is operational