for Carmichael, CA
PAT - Carmichael, CA
Quick and easy!
KATHRYN - Carmichael, CA
Great customer service and thank goodness it was only the fuse.
Excellent technician, great set
Gary - Carmichael, CA
Phong from Huft was highly skilled, courteous, and informative. Excellent service provider. !
Drew - Carmichael, CA
Excellent prompt and courteous service!
Gary - Carmichael, CA
Chuc from Huft quickly identified and adjusted the problem.
Performed heating tune up for Trane package unit. Tested and checked system in heating mode. Found no issues. Changed 20x30x1 filter. System is operational at this time.
Quoted customer for seal and insulate including craw-space ducting.
Performed heating tune up for Lennox heat pump system. Tested and checked system in heating mode. Found no issues. System is operational at this time.
Performed diagnostic on York split system. System not running on arrival. Everything but gas was coming on. Possibly the board on molex plug. When testing for voltage at molex plug on control board to gas valve, system started working. Looked at back of board and could be one of the solder connections for gas valve.
Performed diagnostic on rheem split system. Found that 60A fuse was bad at air handler. Replaced and tested system. All components working. System went up 2 degree in 20 minutes of run time. Working well now.
Replace existing packaged gas/electric unit with a Trane High Efficiency Two Stage Heat Pump packaged unit. Install Bradford White HPWH Hybrid heat pump water heater. Replace both 14â€ X 25â€ return air grills with High Flow grills, run 220V circuit to the new water heater and EV on garage wall next to electrical panel. Install outlet for existing 220V going to range. Install Ecobee Wi-Fi thermostat. Installation includes all material, labor, taxes and rebate processing. Trane: 4WCZ6048B4. Efficiency: 16 SEER, 12 EER, 8.5 HSPF Warranties: 10 Year Parts and compressor, 5 Year Labor, 2 Year Maintenance Project Cost: $16,511 SMUD Rebate: -$7,500 Paid to HUFT: $9,011 Gary will be paying $2011 and financing $7000 through Synchrony Autho #007147
Replaced 20x25x5 merv 16 filter.
Performed heating tune up for Lennox spilt system. Tested and checked system in heating mode. Found no issues with system. System is operational at this time.
Check system operation and all checks are operating properly.
Quoted new Heat Pump system, Heat Pump Water Heater and all new ductwork.