for Carmichael, CA
Huft Super Heros
DAVID - Carmichael, CA
They are fantastic!
Kris was amazing.
Melissa - Carmichael, CA
Air conditioning repair
Chris - Carmichael, CA
It was Great
Joe - Carmichael, CA
Great Service and Willingness to Educate
YGennaro - Carmichael, CA
Very thorough and easy to speak with. Matt took the time to look at our home’s needs and provide us multiple options. Greatly appreciated his willingness to answer my questions.
Fantastic as always
DAVID - Carmichael, CA
Best quality and service in town
Kelly - Carmichael, CA
Huft always great!
Gary - Carmichael, CA
Chris did a thorough semiannual service. Very satisfied.
Daniel - Carmichael, CA
Very good service and fast.
Charles - Carmichael, CA
Excellent and efficient
Replaced a dual capacitor, single capacitor, and blower motor. Also cut in a new vent.
Relocated attic fan fro one end of house to other. Re-routed power.
Preformed diag. on a Goodman system found a bad dual run capacitor 40/5mfd I replaced capacitor tested system is operational at this time also talk to client about hard start kit and club membership denied at this time
Found system not cooling house properly. Checked refrigerant levels and found that compressor is turning on but not working properly. Recommend compressor be replaced for system to operate properly.
Performed an a/c tuneup on all 3 systems. Found bad capacitor on back unit, burnt contactor on upstairs unit, and no hardstart kit on main unit. Replaced a dual capacitor, contactor, and installed a hardstart kit. Also signed up for a super hero club on all 3 systems. System operations ok at this time.
Found system fan working and no amps from compressor checked the dual capacitor and found it read 0mfd. All other checks and components are within manufacturers specifications. System is operational at this time
Found system operating. System has a 14 degree temperature split from supply and return air. The capacitors were all within factory specs. System is not under drastic heat load at this time and the motors are running at max amp rating for the system. Recommend blower motor replacement and cleaning of blower wheel and evap coil. Recommend condenser fan motor due to oil leakage. Recommend charging the system to proper superheat levels to obtain proper temperature split. Recommend comfort advisor to discuss replacement options.
Found system Trane split system low on R410a also found compressor capacitor lower than manufacturer specifications. Replaced capacitor and filled system with R 410 a. System has 20 degree temp split. System is operational at this time.
Preformed diag on a Lennox system I found a bad txv client has parts warranty no labor warranty
Performed diagnostic on split Day and Night. Found condenser fan not working. Capacitor rated 35/5, reading 33.4/0. Replaced capacitor and contactor. Blower moor and evaporator coil are extremely dirty. Recommend exploring replacement options due to 26 year old system, cost of repairs, and inefficiency. Uses R22 refrigerant that as of January 1, 2020 it is no longer allowed to be manufactured or imported.