for Cameron Park, CA
JOE - Cameron Park, CA
Andre was detailed and deliberate in his evaluation of my A/C system.
JILL - Cameron Park, CA
Always very professional and polite.
Performed leak search on system. Found that schrader core on suction line was leaking and i could not tighten it up any more. Replaced and no signs of it leaking. Did not see any dye on indoor and outdoor coil.
Performed ac tune up on Carrier heat pump package system. Tested and checked system in cooling mode. Checked all safeties and connections. Checked filter. Washed outdoor unit. System is operational at this time.
Found bad control board on fan coil unit. Told homeowner to call cal energy because theyâ€™re the ones that installed the unit.
Performed AC tune up on both Trane Heat pump Package unit. Repaired low voltage wiring with electrical taping that was expose to sun causing outer insulation to worn out at upstairs unit as a courtesy. All checks are within manufacturers spec for both systems and are operating properly and ready for the coming season.
Found Trane system low on R22. Found capacitor Is reading lower then manufacturer specifications. Replaced blower capacitor, added R22 and injected dye into system. Need to return in two weeks to perform leak search.
Gave option for 2 ton Goodman with install in 3 to 4 Months
Upon arrival found a Payne ac unit not cooling. Unit is low on R22 Freon. Recommend leak search and new Schrader valves and charging system. Homeowner would like a comfort consultant to come out before making a decision
Performed AC tuneup on a Rheem system there is no air cleaner (Iwave) or surge protection on the system no other issues or concerns at this time
Gave client proposal for el16/el196 system
Performed AC tuneup on a train system system has no air Purification system and the outdoor fan motor is leaking oil no other issues at this time system is operational