for Cameron Park, CA
Performed acsi. All checks ok. Recommend super hero club maintenance to ensure proper performance efficiency. First ac visit was performed today.
Realtor inspection performed on a Lennox dual fuel heat pump system No issues with operation in heating mode system does not have flood prevention switch pressures in heating mode 140/396 outdoor temp 68 degrees Checked system in AC modeR410 a pressure 146/256 disconnect fuse is stuck into disconnect box cannot pull out no other issues or concerns at this time system is operational Recommendations Superhero Club membership Disconnect box Pureairx/flood switch Surge protection
Quoted new 3.ton Goodman heat pump split in attic with all new r-8 flex ducting
Found bad hardstart kit on a Trane unit. Replaced hardstart kit and signed up for super hero club. System operations ok at this time
Quoted new Heat Pump System.
Installed 3 lbs 15 oz r410a. In heated leak seal.. ran tested. System operational.
Performed diag. Found unit low on Freon. Will return with leak dye and Freon.
Install new Lennix heat pump package unit replaced all ducting and registers install new M 3o tsat
Replace existing packaged heat pump with a Lennox High Efficiency Two Stage Heat Pump. Enlarge both return air ducts to 16â€ round R-8 silver jacketed and 20â€ X 24â€ High Flow grill. Replace 9 supply air ducts with R-8 silver jacketed ducting. Install new curb and plenums. Install new Lennox I-Comfort M-30 wi-if thermostat. Installation includes: All material, labor, taxes, rebate processing and permits. Customer wants to put part of the job on a credit card and part with Synchrony 18 months S.A.C. And we will finalize on Monday or Tuesday. Lennox: LRP16HP36P. AHRI #9989613 16 SEER, 12 EER, 8.2 HSPF 10 Year Parts and Compressor, 5 Year Labor, 2 Year Maintenance Project Cost: $16,233. ($188.40 for 120 months @ 6.99% or 18 Months S.A.C.) PG&E Rebate: -$1,600. (Allow up to 4 months for rebate) NET INVESTMENT: $14,633
Client purchased a new packaged Heat Pump System.