for Auburn, CA
Service was very good and all the employees are very nice and professional
Leslie - Auburn, CA
Great service from the office to the tech - we love Chuc
Totally professional and efficient service
VERA - Auburn, CA
Have recommended your company in the last, and will continue to do so, in the future------am always pleased with each service call------your servicemen are superb!
JOHN - Auburn, CA
This company is reasonable and reliable. They service my parents house, since they are elderly I was notified by text when the technician was on his way and was called by him to go over what he did and what was needed so my parents don't have to deal with any of it. I would highly recommend them!
Returned to install new blower motor on system. Tested and checked blower to insure proper operation. Also performed ac tune up for Goodman/Coleman spilt system. Checked all safeties and connections. Changed filter. System is operational at this time.
Found blower motor not turning on when calling for cooling, recommend changing out blower motor, was unable to install stock universal blower motor onto blower housing. Will need to order specific blower motor from manufacture or put in a smaller size universal motor. Will need to reschedule to come back out for repairs.
A/C tuneup completed. Checked a/c operations, all components, and safeties. System operations ok at this time.
A/C tuneup completed. Checked a/c operations, all components, and safeties. Found weak capacitor on blower motor and condenser motor.
Found bad txv on carrier system. Removed sensing bulb to open txv to allow refrigerant flow. Recommend replacing txv valve. All other checks are within specifications and maintenances performed.
Performed annual AC inspection and tune up on Rheem split system. System is operating properly at this time. Today is the last visit. Customer renewed superhero club membership today. Customer also purchased case of filters to be shopped to the house.
Replaced evaporator coil and control board on Lennox furnace. Has a 21 degree temperature split and a 7degree subcool. System is operating properly at this time. All parts and labor covered under warranty.
Performed air conditioning tuneup on 1 of 2 Lennox systems. Downstairs system, all checks are within specifications and maintenances performed. Upstairs system, found bad txv, pressures are reading 245/43. Shuts off on low pressure switch. Need to replace txv. Will call homeowner once part is in hand to set up replacement appointment. Replaced both last free MERV 16 filters. Only downstairs system is operational at this time.
Replace existing packaged gas/electric propane system with a Bosch High Efficiency Variable Capacity Packaged Heat Pump system. Install the Bosch BBC100 Wi-Fi touchscreen thermostat. Install an 8â€ round register at the downstairs bathroom, Repair the kink in the duct going to Ericaâ€™s bedroom. Installation includes: All labor, permits, taxes, material, and HERS Certification with a third party. Customer is going through Synchrony for 18 Months No Interest with Payments. Have the crew flush their tankless water heater out. Bosch: BRB-60HWD1N1-M19. AHRI# 202680590 19 SEER, 10 HSPF 11 Year Parts & Compressor, 10 Year Labor, 2 Year Maintenance Project Cost: $14,000
Performed a maintenance on a Rheem tankless water heater and descale.