for Antelope, CA
Came out the same day I called.
Glenda - Antelope, CA
Excellent service. Courteous and knowledgeable. Very happy with the service.
He was fantastic.
Madeline - Antelope, CA
Merle - Antelope, CA
My airconditioner is 8 years old. the technician said he needed to add 7 lbs of refrigerant and i believed him. So, the checkup went from $87 to over $1000. He then asked me if i wanted him to check for a leak. I said yes. He never told me it would cost another $300 until I got the bill. I thought it would be in the first bill. He was polite, but I was livid. I will not use Huft again.
Over promised and WAY under delivered!! Terible! Be warned
David - Antelope, CA
We dispatched a technician to check out our old AC unit. First technician was very friendly and knowledgeable! We opted to get a quote for a new system or fix the old one. The sales technician arrived and seemed confused as to why he was there. Spent an hour writing up his proposal, didn't say a word. We opted to go with the new system despite the strange sales tech. On the day of install, the helper stepped on and broke our shelves in our attic space, never apologized then say him get into an uber and leave on the job! The technician explained what happened and was nice and finished the install alone. While on walk through we noted the damage (which they did repair) and the vents the salesman told us he took measurements and sent to have replaced... they never arrived. To this day they still do not know if they are supposed to install it or not. Frustrated and will NOT reccomend them!!!!
Fast and direct service
David - Antelope, CA
Larry was nice, professional, knowledgeable on the issue. He had the ac unit open and troubleshot within minutes. We are awaiting further options.
Friendly and informative
KEVIN - Antelope, CA
ScullyRose - Antelope, CA
On time, curtious, great service and reasonably price
Preformed diag on a York system I found a bad 35/5mfd capacitor replaced tested system is operational
Performed AC inspection and tune up on Bryant split system. Customer informed tech about water leaking from the furnace in the garage. Inspected And found the water was coming from the evaporator coil box and leaking into the furnace. Inspected the condensate drain line and found it was full and not draining. Spoke with customer about what I found and recommended having us clear out the drain line. Customer approved repairs. Used nitrogen to clear out the condensation drain. Checked the drain line where it exits the home and verified it is now draining properly. System is operating and cooling at this time. Customer also informed tech that the heating doesnâ€™t work and the furnace just clicks and nothing happens. Customer would like us out in August to check the heating side of the system.
Performed a leak search. Couldnâ€™t find a leak at this time.
Performed ac tune up on Coleman spilt system. Checked all safeties and connections. Washed filter. Washed outdoor unit. System is operational at this time. Renewed on super hero club membership.
Performed pre paid leak search and were not detected any leaks at outdoor coil, indoor coil, and line set. Recheck refrigerant level and was at proper level. Tighten shader core valve.
Found system low on refrigerant and not cooling house properly. Added 5lbs of R410a refrigerant to system. Performed a leak search on system. Found leak in evaporator coil. System is operational at this time.
Second opinion performed I found a lot of 3 and 5AMPS popped fuses in the attic could not find any short or broken wires in the low-voltage circuit system is operational at this time
Quoted new Lennox Variable Capacity Heat Pump System.
Checked a/c operations. Found dirty evap coil and unit low in R22 refrigerant. Possible leak in the system.
A/C tuneup completed. Checked a/c operations, all components, and safeties. Found dirty filter and evap coil.