for Antelope, CA
ScullyRose - Antelope, CA
On time, curtious, great service and reasonably price
Performed sidekick club maintenance. Tested and checked system in heating and cooling mode. Found no issues. Changed 20x20x5 merv 13 filter. System is operational at this time.
Found bad blower motor, rollout switch, and fan limit control. Replaced blower motor. Tenant will repair the fan limit and rollout switch himself.
Performed diagnostic on heat pump water heater. Found that mixing valve was not adjusted properly. Turned to allow more hot water into home.
Bosch 2.0 2/3 Ton Replace existing split gas/electric system with a Bosch 2.0 High Efficiency Variable Capacity heat pump system. Install Bosch BBC100 Wi-Fi Smart thermostat. Enlarge trunk line going to two back bedrooms to a 10â€ round duct and install a 10â€ X 8â€ X 6â€ Wye with the 8â€ going to corner bedroom. Replace return air grill with a High Flow Grill. Run 220V circuit to the air handler and new Rheem water heater and future stove. Replace gas water heater with a Rheem 50HPWH Hybrid Heat Pump Water Heater. Installation includes: Title 24 HERS certification with a third party including duct leakage testing, new fused disconnect with weather tight whip, line set flush with RX-11, overflow safety switch at secondary condensate drain, all material, labor, taxes, permits and rebate processing. Customer is paying cash. Installation for 2/13 and 2/14. Bosch: BOVA-36HDN1-M20G, BVA-36WN1-M20 AHRI# 202868496 20 SEER, 10.5 HSPF 11 Year Parts and Compressor, 10 Year Lab
Checked a Lennox system Upon arrival system was showing error code 276 I checked system I found no issues at this time I cleared the code told client if it comes back to give us a call system is operational at this time
Heat tuneup completed on a Lennox furnace. System operations ok at this time.
Performed system Inspection. Found High Gas Pressure Furnace, readjust to spec. No visible sign of Heat exchanger damage at this time. Secondary pan could use a Flood switch; recommend installing a Flood Switch. Refrigerant level for Cooling is balanced. Found system was without Surge protection; suggest installing a Surge protectors for both outdoor and indoor. Attic Insulation was at an average of 12â€ deep an average of R-25. System operating properly for both Heating and Cooling.
Performed club ahsi on split lennox heat pump system.
Heat tuneup completed on a Lennox furnace. Checked heat operations, all components, and safeties. System operations ok at this time.
Remove and replace existing water heat. Existing water heater is a 40 gallon gas water heater. New water heater will be installed to building code or above. Thank you for your business.