for Acampo, CA
Courteous and conscientious
JUDY - Acampo, CA
Performed AC tuneup on Lenox system. Changed air filter (merv 16x25x5) System is operational at this time.
Performed ac tuneup on a Rheem package unit. Compressor LRA is at 121 amps. Manufacture specifications recommend 117 amps or lower. All other checks are within manufacture specifications and the system is operational at this time. Recommend installing a hard start kit to lower compressor start up amps and prolong the life of the compressor
Replaced air handler control board and set dip switches properly. Found zone board not wired properly. Wired up properly. Tested system and working well now.
Installed new control board and it was defective need to order another control board and come back to install it.
Upon arrival found bosh blower motor not working. Found a bad zone board and air handler control board. Under warranty parts ordered.
Customer doesnâ€™t want anyone in home till the virus is over. Changed filter for homeowner. No charge part of agreement. Will call when the virus is over and feels comfortable with tech inside the home
Reset water heater. Ran tested. Water heater functioning correctly.
Performed furnace tuneup on a Lennox furnace. Replace merv13 16x25x5 filter for homeowner. All checks are within manufacture specifications and the system is operational at this time
Quoted new Lennox High Efficiency two stage packaged air conditioner/furnace.
Completed heating and air heat pump final mechanical paperwork delivered.